Please provide a ________ (H) x ________(L) prefabricated modular dividing wall for interior / exterior use manufactured by Allied Modular Building Systems, Inc. or equal. Building is shipped disassembled with all hardware for onsite assembly. Wall thickness will be from 3-1/2" to 8" thick depending on application. Please provide wall thickness with quotation.
Please provide me with installation, delivery, and pre-wire for the above structure. This includes all travel, installation, labor, and any other expenses that may be incurred to install the walls, doors, ceiling and other non-electrical items.
Please provide me with all electrical wiring of all outlets, lights, switches, and any other electrical components that is required on this project. All concealed electrical shall be incased in flexible aluminum or steel conduit. All exposed conduit shall be incased in steel conduit.. If wiring to the load center / Sub panel shall be wired to breakers that are also provided. All wiring must be field-tested. All wiring shall be completed with 12 Ga. minimum THHN Type and shall comply with all N.E.C. requirements. All circuits shall be 20 amp single pole or 20 amp 2-pole breakers. A ground wire shall be pulled to all outlets, and any other electrical component. This does not include main electrical hookup or phone and data jacks to the main board.
Modular Wiring is not acceptable.
Please provide freight to our plant. This includes all freight charges from your facility to ours. Any damages or freight claims filed by the shipper. No additional purchase orders for damaged materials will be accepted. The recipient shall incur no costs for freight claims. This shall include all charges for freight, damage, insurance, fuel surcharges and any other costs that may be incurred. This does not include unloading at the destination facility.
2.1 WALL PANELS
The wall shall be 3-1/2" 8" actual thickness minimum non-combustible. Panels shall be modular and interchangeable with a minimum thickness of 3-1/2"overall width. The panel shall consist of an insulated polystyrene core permanently laminated to a non-combustible pebble textured aluminum face and shall be permanently applied at the factory and shall be easily cleanable. Wall panels shall be tongue and groove type with vertical channels being placed where electrical requirements are needed. The panels shall be fully fabricated at the factory for easy installation. No splicing shall be necessary for any panels under 20 total height. Must meet a class "A" or class 1 fire rating which requires a minimum of 0-25 flame spread.
2.3 BASE TRACK
The base plate shall be anodized aluminum or painted channel with a minimum thickness of .080. The base channel shall be anchored at 24" O.C. with _" x 3-1/2" minimum embedment. Anchors shall be included with materials. Steel channels will not be accepted.
2.5 POST & FRAMING
Posts shall be anodized aluminum framing channels with minimum temper strength of 6063-T5. The posts will allow for a load to 3,500 lbs. but not to exceed 4,000. Each and shall be an intricate part of the structure. The connecting posts shall serve as an electrical raceway accommodating electrical, data and phone. The raceway shall bear a UL approved sticker and conform to all UL reports. No other posts will be accepted.
2.6 WINDOWS - SINGLE PANE
Windows shall be installed in panels per customer drawing: Windows shall be of the picture-window type and sliding window per customer drawing. The window glass shall be a minimum 3/16-inch thick clear, tempered safety glass pre mounted in an steel frame. Windows shall be a nominal 40 inches in height and extend across the full width of its supporting panel. The windowsill height shall 41 inches from the floor. The sliding windows shall be able to slide sideways. The sliding windows shall have locks, lockable from the inside of the modular wall. Weather stripping shall also be provided with the sliding windows.
2.7 WINDOWS - DUAL PANE
Windows shall be installed in panels per customer drawing: Windows shall be of the picture-window type and sliding window per customer drawing. The window glass shall be a minimum 3/16-inch thick clear, tempered safety glass pre mounted in an steel frame. A 3-1/2" air gap shall separate the two pieces of tempered glass for optimum sound and temperature control. Windows shall be a nominal 40 inches in height and extend across the full width of its supporting panel. The windowsill height shall 41 inches from the floor. The sliding windows shall be able to slide sideways. The sliding windows shall have locks lockable from the inside of the modular office. Weather stripping shall also be provided with the sliding windows.
2.8 PANEL CAPS
Anodized aluminum panel caps or manufacturers standard panel caps incorporating a vertical fascia shall be installed securely on the top perimeter of the wall panels. The panel caps shall provide a neat appearance where the wall panels and roof deck come together.
Standard Timely frames shall be provided for all openings. All doors shall be pre-hung at the factory and assembled into panels to ensure easy installation and proper fit. Doors shall be a nominal 36 inches wide by 80 inches high and have thickness of 1-3/4 inches. The interior and exterior finish of the doors shall be color coordinated with the finished wall. The exterior finishes of the wall panels and has the same finish on both sides.
SPECIFY DOOR TYPE.
Hardware shall be high quality AMBS Standard.
8.2 ELECTRICAL OUTLETS
Wall outlets shall be standard 110-volt AC duplex outlets. Wall outlets shall be located as shown on drawings. Wall outlets shall be a nominal 18 inches in height from the floor. Outlets shall be provided with cover plates. Light switches shall conform to the National Electric Code.
All materials and workmanship shall be guaranteed to be free of manufacturing defects for a period of 10 years from the date of shipment. For items not manufactured by Allied Modular, the manufacturers warranty applies. Installation warranty shall be 1 year. Installation is not covered under warranty unless provided by Allied Modulars Factory Trained Installers.